|Place of Origin:||china|
|Model Number:||A 556 / A 556M|
|Minimum Order Quantity:||5 Ton|
|Packaging Details:||Packing in wooden, hexagonal box or other seaworthy ways|
|Delivery Time:||30 days|
|Payment Terms:||T/T L/C D/P D/A WesternUnion MoneyGram Others|
|Supply Ability:||60000 Ton/Year|
|ID:||5mm-12mm||Material:||Carbon Steel Tube|
seamless steel pipe,
seamless carbon steel tube
A 556/A 556M Cold-Drawn Carbon Feedwater Heater Seamless steel Tubes
1. Referenced Documents
1.1 ASTM Standards:
A 450/A 450M Specification for General Requirements for Carbon, Ferritic Alloy, and Austenitic Alloy Steel Tubes E 30 Test Methods for Chemical Analysis of Steel, Cast Iron, Open-Hearth Iron, and Wrought Iron
2.1 Manufacture—Tubes shall be made by the seamless process and shall be cold drawn.
2.2 Heat Treatment:
2.2.1 Cold-drawn tubes shall be heat treated after the ﬁnal cold-draw pass at a temperature of 1200°[640°C] or higher to ensure ductility satisfactory for rolling into tube sheets and to meet mechanical properties as speciﬁed.
2.2.2 If stress-relief anneal of the U-bends is speciﬁed, the anneal shall consist of heating the bent portion within a range of 1100 to 1200°F [585 to 640°C].
3. Chemical Composition
3.1 The steel shall conform to one of the requirements as to chemical composition as prescribed in Table 1. 3.2 When a grade is ordered under this speciﬁcation, supplying an alloy grade that speciﬁcally requires the addition of any element other than those listed for the ordered grade in
|Grade A2||Grade B2||Grade c2|
4. Permissible Variations in Dimensions (Fig. 1)
4.1 Permissible variations from the specified outside diametershall not exceed 0.004 in. [0.10 mm] for tubing under1.0-in. [25.4-mm] outside diameter nor 0.006 in. [0.15 mm]for tubing 1.0 in. [25.4 mm] to 1.25 in. [31.7 mm] inclusive.These tolerances do not apply to the bent portion of theU-tubes. At the bent portion of a U-tube for R = 2 D orgreater neither the major nor minor diameter of tube shalldeviate from nominal by more than 10 %. If 1 ⁄ D is specified,tolerances could be greater.
4.2 Permissible variations from the specified minimum wallthickness shall not exceed +20 % or −0. The wall thickness of
|Grade A2||Grade B2||Grade C2|
|Tensile strength, min, ksi [MPa]||47||60||70|
|Yield strength, min, ksi [MPa]||26||37||40|
|Elongation in 2 in. or 50 mm,
min, % (longitudinal)
|Grade A2||HR B 72|
|Grade B2||HR B 79|
|Grade C2||HR B 89|
the tube in U-bent section shall be not less than valuedetermined by:
tf T 2R / 2R D (1)
t = wall thickness after bending, in. [mm],
T = specified minimum tube wall thickness, in. [mm],
R = centerline bend radius, in. [mm], and
D = nominal outside tube diameter, in. [mm].